OUTPUT Control,Alarm or Logic Output. Universal Process Input. 0 to 50 mV Z. 0 to 20 mA Z. 0 to 10 V Z. Pt CAT II. Y c. ESM MODULE – 2. NC. is done with it ‘s selectable ON-OFF, P, PI, PD, PID,. AutoTune and Self Tune PID properties. ESM, ESM ESM, ESM ESM eng esm 02 v04 07_14_ Home; eng esm 02 v04 07_14_ Anterior. eng esm 02 v04 07_14_
|Published (Last):||23 May 2005|
|PDF File Size:||13.90 Mb|
|ePub File Size:||1.13 Mb|
|Price:||Free* [*Free Regsitration Required]|
If there is danger of serious accident 44950 from a failure or defect in this unit, power off the system and seperate the electrical connection of the device from the system.
This parameter determines which value is shown in top display. This must be selected if analogue input module in Module-1 socket is EMI Tampering with the unit may results in malfunction, electric shock or fire. Eam not clean the case with hydrocarbon-based solvents Petrol, Trichlorethylene etc. Minimum process input value in Pt and Tc inputs. Cooling output can not be active less than this parameter. It’s a community-based project which helps to repair anything.
Alarm- 3 hysteresis value. If you have any of these parameters 49950 observed 2. Defines maximum value for selectable dual point calibration.
If motorized valve control is selected this parameter is active ON The minimum duration of the valve motor drive output 0. Use power switch and fuse as required.
This warranty is in force if duty and responsibilities which are determined in warranty document and instruction manual performs by the customer completely. Warranty EMKO Elektronik warrants that the equipment delivered is free from defects in material and workmanship. Sensor connection is wrong or there is no sensor connection. It determines operation form of hysteresis. If this parameter 0. Blinking can be canceled by pressing Enter button.
If analogue input value is less than minimum value of operating scale top display starts to blink. It is active if logic output function of Output-3 is alarm output. It can be adjusted from 1 to Never attempt to disassemble, modify or repair this unit. Unit selection Configuration of analogue input module in Module-1 socket. User can do defined 16 display adjustment points.
Process Control Devices : EDA Intromit
This parameter is used for shifting the proportional band. If the condition is not true, integral value is not calculated and last calculated integral value is used. This parameter is visible if one of the analogue input modules is plugged in Module-2 socket Alarm on delay time 0, Seconds It is active if logic output function of Module-1 is an alarm output Alarm off delay time 0, Seconds Alarm off delay time.
Even if this parameter is 0, this parameter is accepted 50 msecs for security. It can be adjusted from to seconds. If it is 0, derivative control part does not perform. Value between 5 and seconds can be entered. Process Inputs Universal Input: It is your responsibility to ensure that qualified mechanical and electrical technicians install this product. It is active if process input of Module-1 is TC input. It can be adjusted from 0 to When tune operation finishes if this parameter is 0, it can not be changed because derivative control part does not perform.
Real time is stopped Motorized valve control is deactive Motorized valve runs with heating PID function. Operator can see operator menus and parameters but operator can not change the parameters. In package- One piece unit – Twopiece mounting clamp – One piece instruction manual AUTO Maintenance Repairs should only be performed by trained and specialized personnel.
If it is no password protection while entering to the technician Parameters. This parameter is visible if one of the analogue input modules is plugged in Module-1 or Module-2 socket Measurement input selection for Output-3 alarm output. Motorized valve runs with cooling PID function. The unit is normally supplied without a power switch exm a fuse.
Even as a result of the cooling PID calculation device calculates esmm output value less than this parameter, cooling output is active minimumor OLLC parameter. Maximum 10 Ohm Sensor Break Protection: The unit normal to return to work, the device energy cut-off and Analog Input one of the modules must be removed. Do not do the montage of the device with inappropriate fixing clamps. PT input type selection.
Keep the power off until all of the wiring is completed so that electric shock and trouble with the unit can be prevented.