This method is included in NEMI for informational purposes as it is approved by EPA for regulatory use. Detailed information on this method is not currently. eropoly acid. This is reduced to silicomolybdenum blue that is determined pho- tometrically. The method is analogous to APHA SiO2 D+E, ASTM D, . Find the most up-to-date version of ASTM D at Engineering
|Published (Last):||7 December 2017|
|PDF File Size:||4.8 Mb|
|ePub File Size:||6.57 Mb|
|Price:||Free* [*Free Regsitration Required]|
Under certain conditions, silica forms troublesome silica and silicate scales, particularly on highpressure steam turbine blades. The mean and standard deviation of the seven values should then be calculated and compared, according to Practice Dto the single operator precision and recovery established for this Test Method.
For measurements at nm, plot absorbance versus milligrams SiO2 per litre. Silicon is the most abundant element in igneous rocks and is the characteristic element of all important rocks except the carbonates.
High blanks, nonlinear calibration curves, and poor reproducibility have been observed with some batches of this compound. The values obtained must fall within the limits speci? It is applicable to most waters, but some waters may require filtration and dilution to remove interferences d895 color and turbidity. Complex silicate residues that do not yield to this treatment are dissolved by alkali fusion and dehydrated with HCl.
In cooling water systems, silica forms deposits when solubility limits are exceeded. Reagents and Materials NOTE 3—Store all reagents to be used in this test method in polyethylene or other suitable awtm bottles.
Refer to Appendix X1 for historical information. Link to Active This link will always route to the current Active version of the standard. Quality Control QC Due to the complexity of silica chemistry, the form of r859 measured is defined by the analytical method as molybdate-reactive silica.
It is particularly applicable to treated industrial waters. Referenced Documents purchase separately The documents listed below are referenced within the subject standard but are not provided as part of the standard.
Since the method includes an evaporation step, the applicable concentration range depends upon the volume of sample used in the determination. The CVS is a solution of the method analyte of known concentration mid-calibration range used to fortify reagent water.
After dissolving, add the solution to mL of a solution containing 30 g of sodium hydrogen sul?
ASTM D – 16 Standard Test Method for Silica in Water
The analyte recoveries for the LCS should fall within the control limits of x 6 3S, where x is the IDP amount and S is the standard deviation of the mean recovery established from Link to Active This link will always route to the current Active version of the standard.
In contrast, silica may be added as a treatment chemical in some systems, for example, in corrosion control. Ast, test method is useful for concentrations as low as 20? The presence of most silica in natural waters comes xstm the gradual degradation of silica-containing minerals.
Standard Test Method for Silica in Water
Longer path length cells 40 to 50 mm are recommended for concentrations below 0. Users of this astk are expressly advised that determination of the validity of any such patent rights, and the risk of infringement of such rights, are entirely their own responsibility. A superscript epsilon e indicates an editorial change since the last revision or reapproval.
Unless otherwise indicated, it is intended that all reagents shall conform to the speci? In contrast, silica asstm be added as a treatment chemical in some systems, for example, in corrosion control. The type and composition of the silica-containing minerals in contact with the water and the pH of the 8d59 are the primary factors controlling both the solubility and the form of silica in the resulting solution.
Historical Version s – view previous versions of standard Translated Version s: The lower limit of this method is 5 mg of silica.
ASTM D859 – 16
The level 2 spiking solution used for the precision and bias study is a asgm IDP solution. Your comments will receive careful consideration at a meeting of the responsible technical committee, which you may attend.
Those forms of silica that are molybdate-reactive include dissolved simple silicates, monomeric silica and silicic acid, and an undetermined fraction of polymeric silica.