Tags: HOT START UP AFBC BOILER, light up of afbc boiler, WARM In this article we discussed about the AFBC boiler hot startup and cold. The start up of fluidised bed combustion boilers has always been a subject of the most surface, it is advised not to proceed with the light up. Unless the top. Requirements of Bed material,Charcoal & Diesel. Bed material Maximum Particle size Bulk density Chemical composition MM TO
|Published (Last):||20 April 2010|
|PDF File Size:||14.67 Mb|
|ePub File Size:||19.92 Mb|
|Price:||Free* [*Free Regsitration Required]|
Boiler Ilght – Afbc Documents. Ensure all personel were cleared. Measure air box pressure P1 MM of wc 3. Main steam stop and pilot valve.
Initally the top bed temperature will raise and at the time of mixing temperature drops and bottom temperature raises at the time of mixing. Maintain drum level at normal recommended level. Published on Oct View 3. C and stable the boiler. Fuel feeders and controllers.
AFBC ( Atmospheric Fluidized Bed Combustion ) BOILER COLD START UP PROCEDURE – ASKPOWERPLANT
Feed pump and drives. Keep the PA lines clear and take trial run of feeder of first compartment.
Close the bed superheater drains. Cfbc boiler operation procedure? Once fludisation study is completed boiler is ready for light up. Check the following equipments for adequate lubrication.
Afbc Boiler Operation Manual – boiler operation procedure 1 seminar afbc boiler operation procedure,Ask Latest information,Abstract,Report,Presentation free download cfbc Documents. Check the bed material and fludisation study is being done. Start the LD oil pump and maintain the oil pressure between 6.
Afbc Boiler Operation Afnc – ante-annum.
Ensure all access doors are closed. CFBC boiler operation procedure? The air flow at which fludisation starts is noted and will be maintained at the time of mixing. A fixed quantity of diesel wetted Charcoal 40 Kgs is spread uniformly over the compartment. Valves on feed line connecting to feed pumps operation.
Afbc Boiler Light Up Procedure
Check the following valves are kept in open condition. Drum and main line vent.
Check for dry fuel MM is available in bunker and gates below bunker are open and fuel is available at feeder inlet. Check the following valves in boiler are in closed condition. Start up vent valve. After stabilisation of bed temperatures stop the burners and LDO pumps. The pressure drop across bed is obtained for various air flow.
Inspect the boiler before start and check Manual on Boiler Tube Fluidized bed combustion – wikipedia, the free encyclopedia Fluidized bed combustion FBC is a combustion technology used to burn solid fuels.
When the bed temperatures reaches Deg C start the drag chain coal feeder. Drain valves of water level gauge. Shiatsu Massage Manual Afbc boiler boiler, The Light up all the four burners. C and start the ash handling system.
Add gas plenum pressure P2 Furnace draught to P1.