Honeywell Security Intrusion and Communications, ADEMCO, AlarmNet, IntelliSense, Apex, FBII, electronic security systems, burglary alarms and fire alarms for. Installation manual for the Honeywell wireless three-zone sensor. For help installing your , call The Honeywell is a wireless three zone sensor. Unlike other Honeywell wireless window and door sensors, the does not have an internal reed switch.
|Published (Last):||16 March 2006|
|PDF File Size:||9.5 Mb|
|ePub File Size:||7.4 Mb|
|Price:||Free* [*Free Regsitration Required]|
If concealed wiring is to be used, feed it through the slot in the case back but do not connect. If concealed wiring is to be used, feed the wires through the concealed wiring entry hole at.
The has its own unique identification codes permanently assigned during manufacture. Add to my manuals Add. The description that follows assumes that the unit will be mounted as shown in the diagrams. For UL installations with fire zones, the position 4 ON setting must not be used. The locking tab will click as the case zdemco locks in place.
Wiring Connections; Specifications – Honeywell ADEMCO Installation And Setup Manual [Page 2]
This warranty replaces any ademfo warranties and is the only warranty made by Seller on this product s. The should be treated as “RF” i. Don’t have an account? Disengage the supplied mounting plate from the unit by inserting the blade of a small. Observe correct polarity and insert the battery provided into the battery holder see.
Mounting For proper orientation of the unit in relation to its wall mounting plate and the loop wiring, read all of this section before installing the unit. For this application, the alignment guide strip along one edge of the plate 5187 no function and may be broken away, if desired. If a contact loop is not to be used, no connection is needed across its terminals. The installer should assume the responsibility of developing and offering a regular maintenance.
Except in the case of the position 4 ON setting, the Auxiliary loops are not affected by. Do not recharge, disassemble, heat above. Regular maintenance and inspection at least annually by the installer and frequent testing by. Surface wiring 58117 enter via the thin “breakout” area provided in. Got it, continue to print. Attach the case back to the mounting plate by sliding the keyhole slots in the case back down.
The Multi-Point Universal Transmitter may have three contact loops connected to it. Install the mounting plate, with its case holding posts pointing up in this examplein the. Page of 2 Go.
No increase or alteration, written or verbal, of the obligations of this Limited Warranty is authorized. Enter text from picture: Dispose of used batteries promptly. Customer understands that a properly installed and maintained alarm system may only reduce the risk of a burglary, robbery, fireor other events 581 without providing an alarm, adekco it is not insurance or a guarantee that such will not occur or that there will be no personal injury or property loss as a result.
The Primary Loop has several DIP switch selectable options that determine its connection requirements, response, and transmission characteristics see DIP switch setting table on next page. The unit may, however, be installed in any direction, as long as the relationship of the unit to its mounting ademfo is maintained.
When a satisfactory location is found, remove the battery and proceed with installation. Recommendations must be included for a specific.
Although two holes are provided in the unit that would permit mounting directly to a surface holes “A” in Diagram 2it is recommended that the mounting plate be used, as described below, for ease in removing the unit for servicing should it become necessary. A built-in cover tamper switch is activated when the cover is removed. Complain wrong Brand wrong Model non readable.
Honeywell ADEMCO 5817 3 Point Wireless Transmiter
For UL installations, no contact in any of the loops may be more than 3 feet from the transmitter. The open slot at the other end of the unit cannot be used as a cover pry-off. Remove the transmitter’s cover if not already off as described adeemco Mounting Step 1. Don’t show me this message again. It is not necessary to program the transmitter IDs during installation.
Disengage the supplied mounting plate from the unit by inserting the blade of a small screwdriver into the locking tab release window see Diagram 2 and pressing it against the case locking tab see Diagram 1 while sliding the plate downward along the case back.
Honeywell ADEMCO 5817 User Manual
By pressing ‘print’ button you will print only current page. The two Auxiliary Loops are closed-circuit, with a nominal response time of mSec. Seller shall have no obligation under this Limited Warranty or otherwise if the product s is altered or improperly repaired or serviced by anyone other than Honeywell factory service. With the battery still not inserted, connect the loop wiring to the unit’s terminals see Diagram 2.