ABB SACE. SACE ATS AUTOMATIC TRANSFER SWITCH. SACE ATS Before using the ATS, read Chapter 1 “Safety notes” very carefully to avoid. For this reason, ABB SACE has developed ATS (Automatic Transfer Switch) – the solution for automatic mains-generator group transfer, able to manage the. ATS Control Product from ABB. Check Galco’s stock for ATS Control Product from ABB. Huge Inventory – Same Day Shipping – Expert Technical Support.
|Published (Last):||6 June 2015|
|PDF File Size:||13.94 Mb|
|ePub File Size:||10.65 Mb|
|Price:||Free* [*Free Regsitration Required]|
Use of this manual for any other purpose is specifically prohibited.
What do I need to do? Check that the fuse of the motor operator at the bottom of the switch is ok, that the OMD controller does not show any alarms and that the switch has a power supply. Please select country from the list below. I need more information ABB Sales.
If you require any other information, please contact us using form located at the bottom of the page. Show on map Hide map. OMD controller shows an alarm. You can rest assured that your automatic transfer switch solution works as expected without the need to carry out any testing. On table mount, horizontally ags010 vertically. Ab Spare Parts catalog is now available! AC D M codesys 2.
Ags010 our transfer switches, you are never left in the dark. Transfer switches OTM… A — Easy installation of accessories Save installation time and cost with our transfer switches. The voltage sensing cables are installed inside switch body and cannot be removed or changed. Manual operated bypass switches. English – pdf – Catalogue Transfer, change-over and bypass switches. The locking infromation output feature in the OTM does not work if the motor operarator is not supplied.
Q As a part of ABB abh, a. I need more information ABB Sales. The entire solution has been tested by ABB and is guaranteed to fulfill all the requirements according to the IEC standard.
This means that you need to get the neutral reference from a separate place or use a transformer. Installation and operation instructions. Suggestions ags010 the developers at ABB are confronted with call for a manual motor starter thatdevelopment within the ABB manual motor starter family for motors in a wattage range up to 7.
This means that you need to get it from a separate place and select the option “Neutral in use” from the OMD controller. In no event shall ABB liable for directdocument, nor shall ABB be wts010 for incidental or consequential damages arising from use of any softwarecopied without written per-mission from ABBand the contents thereof must not be imparted to a thirdlicense.
English – pdf – Brochure Switches, Spare parts for motorized change-over switches. Check that you are supplying the motor operator with correct voltage level and that control circuit connections are voltage atz010.
Frequently asked questions 1. Yes but deranting factors needs to be checked.
There was a problem with your request. Go to myABB Logout. For this country please use ABB’s partner contact details.
ABB ATS manual datasheet & applicatoin notes – Datasheet Archive
Rate this page General impression. The product locking information output feature in the OTM does not work. Maintenance and service manual Architecture. Change-over and transfer switches for Critical Power applications.
The only possibility is to do completely new wiring. Motor operator does not react to control command. Go to myABB Logout. In motorized change-over switches from 40 to Amperes OTM40…. We will get back to you as soon anb possible. Where can I get spare fuses for the motorized change-over switches? The version of the manual. Navigate Search Login layouts-flyoutmenu-cart. Ats100, you need to detect what the reason for the alarm is and shut xbb off – to check how to do it, refer to the user manual.
Main catalogue – Change-over, bypass and transfer switches Technical data, ordering information and dimension drawings of the entire range of manual and motorized change-over, transfer and bypass switches. Check the operating mode of the OMD controller.
Learn more I agree. The Automatic Transfer Switch does not change its position even if both networks are available.